20 Most Recent
Questions & Answers
High cool and low cool not working
Pls check the following....
1) Fix the wire connector to Reversing vale
2) Check the Capacitor if this a low capacitance or (open) not function using Multi-tester.
3) Check the Selector switch if this is not function using Multi-tester . or check the PCB Board (if electronic your units) replaced the Board.
If not yet,go to the nearest repairman to repair that units.
Thank you,have a nice day.
on Jan 16, 2015
The unit is blowing cool
Sorry to read about your problem, I hope this helps you out.
You can have a couple of issue's, one of them is a reversing valve, or even a defective control.
Its takes special tools and equipment to work on this unit.
I suggest you contact a service company.
I tried to help you. Please help me and Rate/Vote on my response. We take the time to answer your question's. take the time to rate us.Thanks and good luck
4 Thumbs - Very Helpful
3 Thumbs - Helpful
on Jan 04, 2011
sounds like ur board is gone out and needs replacing if u dont no about these units i dont advise trying to do this trust me save urself some money and headach and call a tech
on Feb 24, 2010
I have a amana ptac through the wall unit. the
several things could be the cause but lets start with the easiest first. check the filter to see if it is clean. if so then you need to see if the coils behind the filter are clean. a blockage of air flow will cause the unit to freeze up. If the coils look dirty then you can purchase a coil cleaner (aerosol) from a home improvement store or an a/c supply house and follow the directions on how to clean. These coils should look nice and shiny. If all of the above mentioned are in good shape then you possibly have a low charge of freon in the system. In that case an a/c tech will bee required since the usage of freon is only to be done by certified techs.
Hope this helped
on Feb 21, 2010
Amana ptac constantly freezes
in heating mode find sensor located on coil follow to board connection usually 24v and dft terminal jump out with a wire and jump test pins if goes into dft then sensor bad if not board
on May 11, 2009
Replacing an amana mercury thermostat with honeywell programmable. Old wires are y1,w1,w2,g,rc/rh. Have y1 to y, w1 to o/b, w2 to aux, r to r, g to g. Now outside will not shut off when heat is on.
What is -the outside?
Heat pump, gas, electric heat combination?
You may need to back track, double check the Honeywell configuration jumper or software settings for your type of heating used.
Amana Heating &...
on Nov 09, 2019
Not finding what you are looking for?