Question about Powerware Computers & Internet
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
After you replaced the batteries did you perform a manual battery test?
If not do so.
Posted on Mar 03, 2009
If you battery packs are all at 130volts DC, then all of the packs will have become dead, and the batteries are not recoverable. Your battery DC bus voltage on a Powerware 9355 20 to 40kVA rated UPS is nominal 432 volts DC - 36 batteries in series in each string at 12 volts DC per battery. If batteries go below 10.5 volts DC each, or 378 volts DC bus voltage, no amount of charging will recover these batteries. You should not be recycling the DC battery breaker, unless you felt the battery breaker was faulty. The UPS would have given you an alarm message of either battery breaker Off, Charger Failure, or Low DC Bus Voltage long before the these batteries failed.
The battery test will not proceed if the batteries are dead.
Posted on Feb 11, 2011
Tips for a great answer:
Feb 12, 2015 | Powerware Plus 36 UPS System
Sep 25, 2014 | Powerware 9120 UPS System
Jul 14, 2014 | Powerware 9120 UPS System
Jun 12, 2011 | Powerware 9120 UPS System
Feb 24, 2010 | Powerware 9120 UPS System
Feb 03, 2010 | Powerware 9355 UPS System
Apr 09, 2009 | Powerware 9120 UPS System
Mar 03, 2009 | Powerware 9120 UPS System
Jan 09, 2017 | Powerware Computers & Internet
28 people viewed this question
Usually answered in minutes!