Question about Cooper Wiring Devices Combination Switch & Receptacle
How many sets of wires are coming into the box?
If the box is in the middle of the circuit you will have a power-source black & white wire coming in and a power-source black & white wire going out. And in this case for the switch - there must be a black and a white wire going to a light.
Typically with a switch/outlet combination all the white wires will splice together with a white pig-tail wire to feed the neutral side of the device. The two black wires from the power-source will splice together with a black pig-tail and feed the hot-side of the device. The black wire going to the light will go on one side of the switch.
Looking at outlet/switch device from the front the large slot side of the outlet will be the neutral side and the smaller outlet slot will be the hot side. The neutral side screws will be steel colored and the hot side screws will be brass colored. The white wires will go to the neutral side steel colored screws, and the black wires will go on the hot side brass colored screws on the outlet.
The black wire comig into the box from the light is called a switchleg and goes to a brass screw on one side of the switch. The brass screw on the otherside of the switch will be for the black wire coming from the power-source.
Hope this helps - and please:
TURN THE BREAKER OFF BEFORE YOU START WORKING WITH THE WIRES!
Posted on Mar 16, 2011
Testimonial: "Solution was well-written, very understandable for a novice. Instructions and diagram given with the Cooper device wasn't nearly as good as this. "
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 05, 2013 | LEVITON 109-05225-WSP SWITCH SP W/GD...
Apr 17, 2013 | Pass & Seymour #691CC6 Comb...
Mar 18, 2013 | Leviton 15a 120v Sp Switch
Feb 21, 2013 | Leviton 8299 Combination Switch / Smart...
Feb 13, 2011 | Cooper Industries Cooper Wiring 274W...
Jan 16, 2011 | Leviton Decora Combination Switch - 5625-I...
Jan 02, 2011 | Cooper Industries Cooper Wiring 274W...
Sep 21, 2010 | Leviton 2-Gang Toggle Device Switch...
Nov 16, 2009 | General Electric GE ELECTRICAL TQD22200X2...
Mar 21, 2009 | Electrical Supplies
535 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: