Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
If you're sure the igniter is good and the controller is sending voltage to gas valve to open, but not to the igniter then, yes, the controller is bad. The only way to know for sure is to remove the igniter's molded plug from the board and test voltage directly at the board. You should get about 100-120 vac to the igniter.
Posted on Mar 25, 2010
Testimonial: "thanks alot i will test that."
Posted on Mar 28, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 06, 2016 | Carrier Weathermaker 8000 Gas Furnace 125k...
Feb 28, 2016 | Carrier Weathermaker 8000 Gas Furnace 125k...
Sep 19, 2017 | Carrier Weathermaker 8000 Gas Furnace 125k...
Dec 28, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 23, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 10, 2008 | Heating & Cooling
Mar 25, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
801 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: