Question about Honeywell HE220A1019 Whole House Humidifier Humidifier
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Can the humidifier's housing for
Hello Which came first the chicken or the egg?The unit will operate perfectly in the supply OR return as I have installed in both.If there is more room & easy service access put it in there.
Posted on Sep 14, 2010
Hello, in order to turn your humidifier on with the furnace the 120 volts coming from your humidifer you must hook it up to a step down transformer, then the transformer will provide 24 volts to you humidistat and solenoid valve. So you need a wire from the HUM on your control board to transformer primary side and a wire from neutral on the board to primary side of transformer. Then you need low voltage wire from secondary side of transformer to humidistat from humidistat to humidifier.
Posted on Feb 20, 2011
Tips for a great answer:
Feb 03, 2013 | Kenmore 14417 Humidifier
Feb 20, 2011 | Honeywell HE360A1027 Whole House...
Sep 27, 2010 | Honeywell HE440A1005 Humidifier
Jan 08, 2010 | Aprilaire 550 Humidifier
Dec 28, 2009 | Honeywell HE260A1010 Whole House...
Dec 29, 2008 | Aprilaire 700 Humidifier
Oct 14, 2008 | Aprilaire 600 Humidifier
Aug 27, 2008 | Aprilaire 600 Humidifier
Feb 13, 2007 | Honeywell HE120 Humidifier
Jan 12, 2014 | Honeywell HE220A1019 Whole House...
101 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: