Question about Honeywell HE220A1019 Whole House Humidifier Humidifier
Won't draw water, solenoid stays hot
Try removing the cover, and manually cycling on the controler switch? Does the solenoid click on, next to the humidifier (the unit with the water line running through it, with wires coming out of it)? If it does click on, is water running down the water pad? It doesn't necessarily drain water when it's working correctly. All of the water SHOULD be getting evaporated into the air return duct.
If it's clicking on, but no water is running out, you should check the water supply saddle valve and make sure it wasn't turned off during servicing.
If it's not clicking on, you should test that you are getting voltage (12v-18v DC) to the solenoid. If you're not, check all wiring connections and make sure they're tight. If you still don't get power, you have either a problem with your control unit/humidistat, your DC power supply, or the control board on your furnace. You may need to call a HVAC technician at that point, depending on your comfort level/skill level in that regard.
When you say the solenoid "stays hot" do you mean it's physically hot to the touch? Hotter than the water lines running into it?
If the solenoid is getting hot, it probably has a bad coil, and if you continue to operate it, you will probably burn up your DC power supply.
If you're getting voltage, you have water pressure, and the solenoid is still not opening, replace the solenoid.
Posted on Jan 06, 2013
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: HONEYWELL HE260
Unless you are using a current sensing relay or sail switch, you need to get the humidifier power from the blower motor supply so it only operates when the blower is on. Since you can manually control the humidifier, there is not a fault with the solonoid.
Unless you are using a current sensing relay or sail switch, you need to get the humidifier power from the blower motor supply so it only operates when the blower is on.
Since you can manually control the humidifier, there is not a fault with the solonoid.
Posted on Oct 19, 2007
Check for 24volts at the valve. Some techs install these so it only comes on when the furnace calls for heat. It should have its own transformer.
Posted on Jan 19, 2009
push sail switch forward by hand to see if that is the problem.
Remove two wires at humidifier and connect them if it starts than it is in wiring, humidistat, or transformer.
Posted on Oct 28, 2009
Tips for a great answer:
Dec 09, 2013 | Honeywell HE220A1019 Whole House...
Jan 22, 2012 | Honeywell HE220A1019 Whole House...
Feb 09, 2011 | Honeywell HE220A1019 Whole House...
Dec 30, 2009 | Honeywell HE220A1019 Whole House...
Dec 28, 2009 | Honeywell HE260A1010 Whole House...
Dec 13, 2009 | Honeywell HE220A1019 Whole House...
Jan 28, 2009 | Humidifiers
Jan 25, 2009 | Honeywell HE220A1019 Whole House...
Feb 26, 2008 | Honeywell HE220A1019 Whole House...
Nov 18, 2007 | Honeywell HE220A1019 Whole House...
480 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: