Question about Carrier Weathermaker 8000 Gas Furnace 125k Btu
The fan runs but the furnace won't release gas when the igniter glows. it glows three times and the furnace shuts down. i have cleaned the tubes, the end of the flame sensor and vacuumed out the dust and debris around the tubes and the panel area. i have also shut down the system as per the panel instructions at least a dozen times. i need help badly.
Here is a link that might help. Even if it glows, it could still be bad, but it needs to prove air flow as well. Carrier Weathermaker 8000 Ignition Problem DoItYourself com Community...
Posted on Sep 20, 2017
Could be a defective gas valve or thermocouple.
Posted on Sep 20, 2017
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
. Several times of recyling power normally brings the furnance up. Though the failure code has always been 31, there are several different behaviour when the blower starts after reset :
a. blower simply creases.
b. there is an attempt to start the heating unit (I hear the high pitch noises), then everything stops.
c. there is an attempt to start the heating unit (I hear the high pitch noises), once I see the orange glow from the coil, normally the gas is lit up and the unit starts working.
Posted on Dec 18, 2007
If you're sure the igniter is good and the controller is sending voltage to gas valve to open, but not to the igniter then, yes, the controller is bad. The only way to know for sure is to remove the igniter's molded plug from the board and test voltage directly at the board. You should get about 100-120 vac to the igniter.
Posted on Mar 25, 2010
Testimonial: "thanks alot i will test that."
sounds like the roll out switch may be sensing a clog. here is a website that can explain things better, hope it helps Tim:
Posted on Oct 30, 2010
SOURCE: carrier infinity 80 won't heat
does your burner flame up and then go put two or three times if so
all you have to do is take out the burner and clean all the soot out of it and then wipe off the sensor
Posted on Oct 09, 2012
Tips for a great answer:
Jun 06, 2016 | Carrier Weathermaker 8000 Gas Furnace 125k...
Feb 28, 2016 | Carrier Weathermaker 8000 Gas Furnace 125k...
Mar 25, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 28, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 23, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 10, 2008 | Heating & Cooling
May 21, 2008 | Heating & Cooling
Mar 25, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Apr 20, 2016 | Carrier Weathermaker 8000 Gas Furnace 125k...
Dec 17, 2014 | Carrier Weathermaker 8000 Gas Furnace 125k...
1,219 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: