Lose of power
Probably, about the time it lost power is when the bearing went bad. The rotor was probably hitting the stator at that point, but the exhaust noise was so loud that you couldn't hear it. As long as it is turning, it will try to produce power, but with the bad bearing, it eventually overheated.
Pramac 5000 Watt...
on Apr 14, 2014
My eg2800 generator is putting out 150 volts, why
Loaded circuit or open circuit? If loaded, brushes need cleaning before buying parts. Check manual for procedure on your model. The brushes are usually culprit. Make sure cleaned and tension springs are free. Use compressed air to clean out armature area where brushes located. Re install and test. If better but not fixed replacement brushes may be needed. If open ckt voltage is high this could be normal. Suggest you email product support to be sure.
Pramac 2800 Watt...
on Jan 22, 2014
Not finding what you are looking for?