Kohler Electrical Supplies - Recent Questions, Troubleshooting & Support
Kohler 12 RES - Unit fails to start occasionally. Attempting a manual start by placing switch in run position, cause a loud click, but no cranking. The panel says CC. This morning I put a jump star
I finally solved the intermittant starting problem on my Kohler 12 RES by replacing the strater and the starter relay. I was also experiencing the occassional OC indication, red blinking LEDs on the ATS, and intermittent non-starts during the weekly exercises. The problem happened during power outages a couple times also. If I flipped the start switch between auto and run quickly the generator would occasionally start. Once started, the generator runs fine. I ordered a new starter, which included the starter solenoid. By the way, don't worry about the genuine part thing..the old starter was a Delco made overseas. I ordered a new starter online for $85 (6744N) and it was indentical to the genuine Kohler starter. Replaced the starter and it improved the problem but did not totally solve the intermittent starting. Ordered the starter relay (GM49746) replaced it and the problem is solved.
Kohler 12 kW...
3 days ago
Not finding what you are looking for?