Question about Sta Rite 3/4 Hp Above Ground Pump Ne640
There is a screened check valve that should be attached to the pick up / suction side of the pump on the very end of the plumbing in the bottom of the well. If you have shut off the water output going to the home / what ever and the pump still drops pressure to zero as soon as it shuts off the shallow well foot valve is stuck open / has failed.
Some systems use both a foot valve and an in-line check valve to prevent the symptom you currently have.
Foot valve example:
If this valve has failed... there is nothing to prevent the contents of the pressure tank from dumping back into the shallow well.
I doubt you have a shut off on the pump suction side but if you do once the pump shuts off close this valve. I would bet your pressure tank holds the pressure. If you do not have a shut off valve... just feel for a rush of water in the suction pipe AFTER the pump reaches pressure and shuts off. If your feeling water flow with the pump off and the tank at pressure / loosing pressure the foot valve is bad.
Thanks for choosing FixYa,
Posted on Apr 18, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 25, 2015 | Utilitech 1-HP Cast Iron Convertible Jet...
May 21, 2014 | Plumbing
May 27, 2017 | General Electric Dishwashers
Oct 28, 2011 | Grundfos MQ3-45 1 HP Pressure Booster...
May 22, 2011 | Grundfos Plumbing
Jan 11, 2011 | 1997 Chevrolet Tahoe
Dec 26, 2017 | Grundfos RCP-96 Recirculation Pump for...
Jul 04, 2009 | Plumbing
Jul 16, 2019 | Poulan Garden
347 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: