Question about Xantrex Technology Heart Freedom 30 Inverter/Charger, 3000w 130a, 81-3011-12
I am assuming that no fault lights are showing on the remote panel, but if they are, then those indicate a problem, e.g. overtemp, or AC overload. If the former, allow the unit to cool down and/or provide more ventilation, and if the latter, reduce the AC load by turning things off. The inverter must be in "standby" mode (green inverter light slowly flashing) for the inverter function to come on automatically when the incoming AC is shut off. Also, the battery bank voltage must be between 10V and 15V for a 12V system, the inline battery fuse must not be blown, and the unit's pop-up breaker (on the right front of the box) must not be tripped.
Posted on Sep 27, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 17, 2018 | Inverter Heating & Cooling
on Mar 03, 2010 | Televison & Video
Jun 01, 2015 | Inverter Electronics - Others
Sep 25, 2010 | Electronics - Others
Jul 06, 2010 | Delta Vfd007b43a AC Drive VFD B Inverter
May 21, 2010 | Kitchen Ranges
Mar 19, 2017 | Tripp Lite PowerVerter APSINT3636VR UPS...
Dec 09, 2009 | RoadPro AC/DC Power Inverter 2000/5000w
Aug 28, 2009 | Xantrex Technology Xantrex Technologies...
Jun 19, 2009 | ABB S272-k16 2-pole Miniature Circuit...
Nov 29, 2011 | Xantrex Technology Heart Freedom 30...
318 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: