Question about Nor-Lake Norlake Refrigeration 4' x 6' Kold Locker Walk-In Cooler - 6' 7'' High w/Floor
Went to start a walk-in cooler after years of down time. The compressor will run for about 10 seconds then shut off for about 30 seconds then run for another 10 & shut off for another 30. Any ideas?
It has lost some freon and is not charged correctly...the unit is pumping down and shutting off on low pressure and then after being off a bit the pressure comes up and it restarts...
Need to check the charge and top it off and you will be good to go..
Posted on May 28, 2010
Testimonial: "Thanx for the good advice."
This walk in cooler was short cycling. runs 10 sec, then shuts off for 15 sec. Was low on freon. Problem was in evaporator coil. All U-bends started to leak, copper corrosion. I end up replacing fan coil. I hope that's was helpful.
Posted on Dec 16, 2018
most likely that walk-in cooler is low on refrigerant (freon). I made video with the same issue. This refrigerator has small leak, i tried to find leak with soap bubbles, but no luck, so end up charging it with freon and add leak dye, so next time I can find that leak for sure.
Posted on Mar 13, 2016
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 10, 2015 | Refrigerators
Sep 29, 2011 | Heating & Cooling
Aug 15, 2011 | Refrigerators
Apr 27, 2010 | Frigidaire 20.3 Cu. Ft. Frost-Free Upright...
Dec 30, 2009 | Nor-Lake Norlake Refrigeration 4' x 6'...
Jan 17, 2009 | Air Tools & Compressors
Mar 31, 2008 | Kenmore 13.7 cu. ft. / 388 liter Upright...
274 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: