Question about Ruud UBHC Air Conditioner
The heating unit will initially blow warm air, but then cool air starts blowing out. Could there be a problem with a coil? Can temporarily fix the problem by shuting off the unit for about 30 minutes and then turn it back on.
One or both heat sequences. Check for coil voltage, then outlet side of both sequencers , if it not there, replace. If v is present when called for; check time delays for accuracy. Could be dropping if contact surfaces degrading.
Posted on Mar 13, 2019
It sounds like unit could be kicking out the low pressure switch or if it is a electric furnace it could be the sequincers
Posted on Jan 24, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 17, 2017 | Amana Heating & Cooling
Jan 27, 2016 | 2000 Chrysler 300M
Jul 09, 2012 | LG LP0711WNR Portable Air Conditioner
Jun 15, 2011 | 2002 Volvo S60
Mar 20, 2011 | Heating & Cooling
Dec 04, 2009 | Amana PTH153B50AJ Heat Pump Air...
Nov 12, 2009 | 1988 Jaguar XJ6
Oct 22, 2009 | 1998 Ford Taurus
May 31, 2009 | Ruud UBHC Air Conditioner
418 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: