Question about Generac 100 Amp 120/240-Volt Transfer Switch #RTSN100A3
After installation, followed installation guide's instructions for manual test. Utility power off. Breakers on Generac panel off. Generator's breaker off. Generator's mode switch set to off. Manually operated transfer switch to down position. Switched generator's mode switch to Manual start ... readout ''cranking, attempt 1'' for a few seconds ... but no cranking whatsoever, whole unit is silent ... then ''RPM Sense Loss'' message.
Verified natural gas pressure is present. Battery's brand new and shows full charge. 12 volts present at lug under red cap by starter. Fuse is good.
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 15, 2014 | Generac Guardian 8kw Standby Generator
Oct 31, 2012 | Generac Power Systems Hammering
Aug 29, 2011 | Square D Qo 200 Amp 40 Circuit Indoor...
Jul 25, 2010 | Generac Power Systems Generac 5525 20 Kw...
Oct 31, 2009 | Coleman Powermate Powermate 5000W...
Oct 30, 2009 | Hammering
Sep 04, 2009 | Generac Guardian 100 Amp Transfer Switch...
Aug 26, 2009 | Hammering
Apr 09, 2009 | Generac 100 Amp 120/240-Volt Transfer...
4,218 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: