Question about Generac Electrical Supplies
If you have some fundamental electrical training/experience.
Fault is displayed when both zero crosses are missing from the controller's input for 1.5 seconds or more. Could be a faulty excitation winding, zero cross circuit, loose wiring, or field boost hardware problem. Same applies here, v1.12 or later firmware should be installed.
Posted on Jun 02, 2019
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 02, 2018 | Honeywell Heating & Cooling
Feb 08, 2016 | Generac Guardian Air-Cooled Standby...
Mar 01, 2015 | Generac 13,000 Watt / 13,000 Watt Home...
Feb 20, 2015 | Generac Guardian 8kw Standby Generator
Oct 15, 2014 | Generac Guardian 8kw Standby Generator
Oct 05, 2014 | Generac Guardian 8kw Standby Generator
Aug 17, 2014 | Generac Guardian 8kw Standby Generator
Sep 06, 2013 | Generac Guardian 8kw Standby Generator
Apr 12, 2009 | Guardian Electrical Supplies
76 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: