Question about Generac Electrical Supplies
I have led lights as well as Generac load shed modules installed to control overload. I can run every light in house and unit will run smooth. Just when the ac kicks on does it sputter and never smooth out
Shouldn't run it at more than 55 amps per leg if single phase.
Engine performance condition may be the cause if we'll below gen set ratings.
Posted on May 30, 2019
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
If this is one of the big "taco cart" portables you need to check that the vent on the gas cap is open when you're running the engine. In the center of the gage on the gas cap is a little knurled knob, turn it counter clockwise (lefty loosey), about a half turn or so and run the generator.
If that doesn't solve your problem add to it here, otherwise please give me a rating I'm trying to build a little credibility here and could use the help.
Posted on Dec 02, 2008
SOURCE: Generac Guardian 15kW Generator
That sounds just about right, if the relay contacts get welded together it sometimes takes out the driver on the printed circuit board. As you found out, 12vdc from 23 to 194 makes the transfer switch move to the Generator position, relay not energized makes the ATS move to the Normal position.
You can make a nice test function by installing a 10 amp contact switch in series with either the N1 or N2 terminals. When the switch is open the generator thinks the Normal power has failed.
Posted on Jan 26, 2009
I work on these every day. Its either gonna be the rotor or stater, the voltage regulator, but most likely its a bad stepper motor which is the throttle motor, or control board. Thats all that could be causing that so its one of those. If its the rotor or stater thats bad it causes the generator to RPM up because it thinks its not producing enough power due to that. I had the same problem with the same one we just fixed and it was the slip rings on the end of the rotor so bad rotor.
Posted on Jul 09, 2009
If the area you live in has alcohol added to their unleaded gas, then you will probably need to rekit the carbuerator. Also check the spark arrestor for plugging up. Try to find a non alcohol, off road unleaded gas for your generator.
Posted on Jan 21, 2010
Tips for a great answer:
Feb 08, 2016 | Generac Guardian Air-Cooled Standby...
Nov 11, 2014 | Generac Guardian Electrical Supplies
Oct 05, 2014 | Generac Guardian 8kw Standby Generator
Aug 16, 2012 | Generac Guardian 100 Amp Transfer Switch...
Feb 25, 2011 | Guardian Electrical Supplies
Mar 02, 2010 | Electrical Supplies
Jan 22, 2010 | Generac 100 Amp 120/240-Volt Transfer...
Sep 04, 2009 | Generac Guardian 100 Amp Transfer Switch...
Sep 06, 2008 | Electrical Supplies
66 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: