Question about Kohler Electrical Supplies
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: ERROR MESSAGES
nthemba- all the error codes you see indicates phone line condition or error at reciving fax's end. For more details you can refer to
Posted on Oct 10, 2008
Your gas pressure is too low and you may not have a large enough supply pipe. You need at least 10 inches of water column with the engine running to operate an LP vapor fueled engine. Because the engine is starving for fuel, its governor opens the throttle to WOT (so it goes to high revs) but there isn't any fuel to make horsepower with so the output voltage falls and the undervoltage alarm trips.
Posted on Dec 03, 2008
OC stands for Over Crank. How long does it take before the genset starts?
Posted on May 07, 2009
The monitoring system of our Kohler propane generator has sent a "UU" message. What does this mean as it causes the generator to shut down 10 seconds after starting? Also how can this be corrected?
Posted on Jun 02, 2011
Tips for a great answer:
Dec 07, 2017 | Kohler Electrical Supplies
Sep 24, 2013 | Kohler 20RESAL - 20kW Home Standby...
Jul 19, 2013 | Kohler Electrical Supplies
Feb 12, 2013 | Kohler Generator 20kw 20res W/ 200 Amp...
Jun 27, 2011 | Kohler 12 kW Emergency Power System -...
May 28, 2011 | Kohler 12 kW Emergency Power System -...
Feb 04, 2010 | Kohler 12 kW Emergency Power System -...
Mar 31, 2009 | Kohler 12 kW Emergency Power System -...
176 people viewed this question
Usually answered in minutes!