Question about Electric Electrical Supplies
Ej341 is a single pole contactor. It makes no difference.
Posted on Apr 21, 2019
The other wire is the positive wire
Posted on Apr 21, 2019
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
GE 15086 is a 7-day programmable timer. It has more wires than spring-wound timer because clock motor runs on 120V circuit, just like ordinary electric clock. The clock on spring wound timer operated by a spring.
If I understand correctly, the old timer has 2 wires. One of these wires is the Hot wire ... and that wire will connect to GE timer black wire.
The other wire from old timer goes to Load ... and that wire will go to GE timer red wire.
Instructions on a lot of these timers say, it timer doesn't work, then reverse the two wires described above ... this is because timer only works when Timer black connects to Hot.
You can also turn on power and test each wire that came off old switch to bare ground wire. When tester lights up, that is Hot wire.
GE timer Green wire connects to bare ground wire.
Moving on to GE timer white wire. This wire is necessary for the clock to run. This wire connects to Neutral wire which is usually white. You can test for Neutral by testing Hot wire to each white wire in box ... when tester comes on, that is Neutral.
If you do not have a white Neutral wire, then connect GE timer white wire to bare ground wire. This is not code, but it will work fine until you hire electrician to run Neutral into box.
Posted on Oct 04, 2010
Switch has 2 wire > one of these wires is Hot and it connects to Timer black wire > the other wire goes to Load and connects to Timer red wire.
If you get these two wires reversed, timer will not run, so switch them. You know timer is running when dial on front of timer rotates with passing time. You can test for Hot wire by taking out switch, separate wires, turn on power, test each wire to bare ground, tester lights up with Hot wire.
Timer white wire goes Neutral. This wire is necessary to run clock inside timer. Locate Neutral wire inside box >> it is usually two or more white wires twisted together and pushed to back of box. If you do not have a Neutral wire, connect Timer white wire to bare ground wire ... until you can hire electrician to run additional wire to box.
Posted on Oct 05, 2010
Tips for a great answer:
Sep 28, 2018 | TORK Hardware & Accessories
Dec 09, 2013 | Fahrenheat Heating & Cooling
May 27, 2012 | Solar Intermatic Single Pole Model Ej341c...
Aug 01, 2011 | Garden
Nov 14, 2010 | Woods 59007 Decora Style 3015105 Minute...
Oct 17, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Oct 05, 2010 | Hardware & Accessories
Oct 03, 2010 | GE Electrical Supplies
Jun 07, 2008 | Jenn-Air JJW8330D Electric Single Oven
142 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: