Question about Heating & Cooling
I have a Carrier Comfort Zone II with 2 controlled zones. The floor with just the sensor controls perfectly. I set that zone at 75 and it stays at 75. The other zone has the actual thermostat. If I set that temperature at 75, it cools to 68 before the unit shuts down. If I raise the set point all the way up to 90, the temperature holds at 73. Do I have a bad thermostat or is there another solution?
Sounds to me like a bad damper or a bad zone panel. Turn tstat off and call for cooling on zone 2. Then see if your still getting cool air to zone 1.( where the main tstat is)
If you need further help, reach me via phone at https://www.6ya.com/expert/thomas_092728000e6acb79
Posted on Jul 15, 2017
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
sounds like your zone control tstat needs calabrated or maybe replaced,in owners manual there should be a section on calibration if not you may have to replace it
Posted on Sep 15, 2009
The stat that works is called the main and the other two are called slave stats. The stats must be set to heat or cool the same as the main. If you want one room to cool and one to heat , sorry. Need to upgrade to auto changeover. Is this AC actally a Heat pump?
Posted on May 06, 2010
Tips for a great answer:
Feb 16, 2018 | Carrier Heating & Cooling
Feb 14, 2015 | Carrier Heating & Cooling
Jul 27, 2014 | Honeywell Motorized Small Rectangular Hvac...
Sep 25, 2010 | Heating & Cooling
Oct 12, 2009 | Carrier 38CKC042 Air Conditioner
Sep 09, 2009 | Heating & Cooling
Aug 03, 2009 | Carrier 38CKC060 Air Conditioner
Jun 24, 2009 | Carrier 38CKC060 Air Conditioner
Feb 18, 2009 | Carrier 38CKC060 Air Conditioner
Sep 04, 2008 | Carrier Heating & Cooling
168 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: