Question about Amana ACD106R Wall/Window Air Conditioner
When i turn on the central air condition, it starts making loud beeping noise that sounds like door buzzer every couple minutes! the noises go away once i turn off the ac. does anyone know what the problem is? thanks!!
It means it has a fault. try resetting unit by switching circuit breaker off and on it might go away
Posted on Jun 04, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: water keeps leaking from central
It's supposed to do that. There should be a drain line on it to direct the water to drain. That line may be plugged up, you'll have to check it out.
Posted on Aug 02, 2008
manually bump the contactor whare the main power comes in with a insulated object isf unit starts then check for call from stat on stat wire from common to red 24v ac transformer good or see if indoor fan comes on next check call from stat common to yellow 24 v then look for low psi switch to see if it has it locked out could be low on gas
Posted on May 09, 2009
Most heat pumps have an auxillary heat. Many are electric auxillary heat with a heat strip in the air handler. A common malfunction is for the electric auxillary heat to operate when the heat pump is set on cool. To confirm this, locate the conductor that runs from the heat sequencer to the connection on the heat strip. You will see this on the top section of the air handler. Use the clamp on part of the amp meter over that wire. If the thermostat is set on cool and the heat strip is drawing amps, it means the heat is coming on while the heat pump is set on cool. There is usually one or two causes for this, either the sequencer is bad or there is low voltage wires usually behind the thermostat or in the air handler closet that are touching that shouldn't be touching.
If this is not the case, if its not a problem of where the heat is coming on with the air conditioner, it could be a case of the reversing valve malfunctioning. The way a heat pump works is it reverses the flow of the refridgerant. For instance, many heat pumps the reversing valve is activated in cool. That would mean that there is a low voltage circuit that activates the reversing valve when the heat pump is in cool. I'm not sure what model/brand your heat pump is, Goodman and Janitrol for instance, the heat pump reversing valve is activated in cool. In any case, if the reversing valve is not operating properly, when the air conditioning is set to cool it will actually be heating. Or you could set it to heat and it may actually be cooling instead of heating. Please check these two items first and if you have any further questions, please let me know. Especially if you know of any additional problems like the evaporater is icing up or if the air handler fan is not operating when it should.
Posted on Aug 31, 2009
Testimonial: "Thank you for your time! "
Several types out there. 99% of them use the same basic wiring.
Red is power from transformer to t'stat. Sometime there is a wire for common from transformer to t'stat too, but not always.
While is for heat. Green is for fan. Yellow is for cooling.
These 4 to 5 wires go on the terminals that are maked with letters: C=common, RH/RC is for power, W=heat, Y=cooling, G=fan.
In most cases, 2 wires from the indoor unit will go to the outdoor unit to power it for cooling. Usually connected to the yellow wired, Y terminal and common or grounded to the unit if the transformer is done in the same fashion.
If you have a heat pump, totally different animal and different wiring too.
Hope this helps you. Good Luck.
Posted on Dec 20, 2009
Tips for a great answer:
Dec 03, 2013 | Dryers
The sound from your refrigerator can be caused due to various reasons,please check this link bellow to troubleshoot your problem:-
Please get back to us if you have further query else please accept the suggestion. Thank you for contacting fixya.com
Thank you for contacting fixya.com
Apr 02, 2011 | Whirlpool Refrigerators
Jul 19, 2010 | Goodman CLQ36AR49 Air Conditioner
Jun 11, 2010 | 1998 Chevrolet Cavalier
Apr 06, 2010 | Kenmore 20.3 cu. ft. / 575 liter Upright...
Jul 13, 2009 | Heating & Cooling
Feb 18, 2009 | 2000 BMW M5
Oct 26, 2008 | Mitsubishi Galant Cars & Trucks
Dec 02, 2007 | Samsung TXR3079 TV
May 31, 2014 | Amana ACD106R Wall/Window Air Conditioner
6,090 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: