Question about Generac 13,000 Watt / 13,000 Watt Home Standby Generator
Need correction info
See my 5/22/12 comments on my "overspeed fault" problem resolution [Generac 43903 standby Generator overspeed indicator on starting] . If it only runs for a few seconds and then quits, you may have a similar condition to the one my unit had. A good technician should be able to diagnose the problem and determine if you have a similar failure to the one I had, or one of the other causes suggested by RSG000.
Posted on May 23, 2012
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I work on these every day. Its either gonna be the rotor or stater, the voltage regulator, but most likely its a bad stepper motor which is the throttle motor, or control board. Thats all that could be causing that so its one of those. If its the rotor or stater thats bad it causes the generator to RPM up because it thinks its not producing enough power due to that. I had the same problem with the same one we just fixed and it was the slip rings on the end of the rotor so bad rotor.
Posted on Jul 09, 2009
Tips for a great answer:
Oct 25, 2017 | Generac Electrical Supplies
Dec 12, 2015 | Generac GUARDIAN Standby Generator 10 kW/9...
Sep 07, 2014 | Generac Guardian Series 8 kW Air-cooled...
Aug 16, 2012 | Generac Guardian 100 Amp Transfer Switch...
Aug 10, 2011 | Generac Power Systems Generac QT02224 22...
Jul 08, 2009 | Generac 13,000 Watt / 13,000 Watt Home...
Jun 22, 2009 | Generac 13,000 Watt / 13,000 Watt Home...
Apr 06, 2009 | Guardian Electrical Supplies
Oct 10, 2016 | Generac 13,000 Watt / 13,000 Watt Home...
2,003 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: