20 Most Recent
Questions & Answers
Adptive intelligent recovery
On the Pro4000 model you hold the 2 arrows until you go into setup mode. Then arrow up ONLY til you get to option 13. The display will read 13 and 1, press the DOWN arrow and it will read 13 and 0. This turns off Adaptive Intelligent recovery. Now hold the 2 arrows til you see the normal display screen. You are done.
I just did this with a Honeywell tech rep on the phone.
on Aug 16, 2019
I have a Braemar Spectrolink
it gets its power from the unit via the data cable. go on the seely international website or the braemar website and they can put you in contact with another dealer in your area. get it fixed while still in warrenty.
on Jul 09, 2019
How to Set time on a rth6500wf
Press Done on the thermostat if you aren't at the home screen. Then press Set Clock/Day Schedule at the bottom left of the touch screen. Then use the up/down arrows on the right to set the time. Press Set Day (second from the right on the bottom of the touch screen) then use the up/down arrows to set the Day of the week. Press Done to exit the set clock menu. (Alternatively, press Set Schedule to continue to set your thermostat to your daily schedule.)
Honeywell has the manual available on their site: http://yourhome.honeywell.com/home/
. Enter the model number in the search box to find the available manuals. See page E36 (28 of the PDF).
I hope this helps.
on Jun 22, 2019
Remote not workin
what's happened here is the cm61 ng and the reciver box have lost there connection you will have to "rebind" them then it will be fine -
THE BINDING OPERATION DESCRIBED BELOW IS REQUIRED IF:
· Any of the system components (room unit or relay box) are replaced
· HC60NG has incorrect or no binding data stored (e.g. when pre-bound system pack components have been mismatched)
· Interference with the RF signal has caused a communication failure
During the binding procedure keep approximately 1m distance between the room unit and the HC60NG
1 Turn off mains supply to HC60NG for 10 seconds. Re-connect supply.
2 Press and hold the HC60NG push button for 15 seconds to reset previously stored data. The red LED will start to flash at 0.1 s on/0.9 s off. Release the push button.
3 Press and hold the HC60NG push button for 5 seconds to enter the binding mode. Red LED flashing at 0.5 s on/0.5 off confirms the binding mode has been entered.
4 Move the CM67NG slider to the OFF position (CM61 push the OFF button) and press the TEMP , TEMP and PROG 1 buttons together. The CM61/67NG will display InSt.
5 Press the i button to send the binding signal. The red LED is switched off on the receiver box to confirm the successful binding operation. If the red light still flashes push the repeat steps 1-3 and press the the i button until binding is successful.
hope this is helpful
on Dec 05, 2018
I installed a new Honeywell
Are you completely sure you have the Reversing Valve wire in the right place? Some reversing valves are powered for heat, some for cool. Make sure you know which yours is, or perhaps change that setting (see the manual) on the thermostat to try it.
ALSO, sounds like the FAN wire may not be in the right place either. Did you carefully note the wire colors on the old stat before you started, or perhaps take a photo?
on Feb 28, 2018
Not finding what you are looking for?