20 Most Recent
Questions & Answers
Amana Air Command 90 furnace LED light blinks 3 times pause 3 times
TRI-COLOR (DSI LED) DIAGNOSTIC TABLE
No. of Red BLINKS
1 Flame sensed when no flame should be present
Verify the gas valve is operating and shutting down properly. Flame in burner assemble should extinguish promptly at the end of the cycle. Check orifices and gas pressure.
2 BLINKS Pressure switch stuck closed/ inducer error
Pressure switch stuck closed. Check switch function, verify inducer is turning off.
3 BLINKS 1st-stage pressure switch stuck open/inducer error
Check pressure switch function and tubing. Verify inducer is turning on the pulling sufficient vacuum to engage switch.
4 BLINKS Open limit switch Verify continuity through rollout switch circuit.
5 BLINKS Open rollout/open fuse detect Verify continuity through rollout switch circuit, check fuse.
6 BLINKS 1st-stage pressure switch cycle lockout If the first stage pressure switch cycles 5 times (open, closed) during one call for heat from the thermostat the control will lockout.Check pressure switch for fluttering, inconsistent closure or poor vacuum pressure.
7 BLINKS External lockout (retries exceeded) Failure to sense flame is often caused by carbon deposits on the
flame sensor, a disconnected or shorted flame sensor lead or a
poorly grounded furnace. Carbon deposits can be cleaned with
emery cloth. Verify sensor is not contacting the burner and is locatedin a good position to sense flame. Check sensor lead for shortingand verify furnace is grounded properly.
8 BLINKS External lockout (ignition recycles
exceeded where flame is established and then lost)Check items for exceeded retries listed above and verify valve is not dropping out allowing flame to be established and then lost.
9 BLINKS Grounding or Reversed polarity Verify the control and furnace are properly grounded. Check and reverse polarity (primary) if incorrect.
10 BLINKS Module gas valve contacts energized
with no call for heat Verify valve is not receiving voltage from a short. If a valve wiring is correct and condition persists, replace module.
11 BLINKS Limit switch open - possible blower
failure overheating limit Possible blower failure, restricted air flow through appliance or duct work. Verify continuity through limit switch circuit and correct overheating cause.
12 BLINKS Module Ignitor contact failure Fault code indicates the module ignitor contacts are not functioning
properly. Replace module.Solid Module - internal fault condition Module contacts for gas valve not operating or processor fault.
Reset control. if condition persists replace module.
3 double 2nd-stage Pressure Switch Stuck Open/Inducer Error
Check pressure switch function and tubing. Verify inducer.
on Feb 02, 2018
When the alarm on the Patton Electric Heater sounds, whay does one do to fix that?
This heater was the determined cause of my total loss house fire. I thought the company would atleast help me find some where else to live, they seem to care. But, as of lately they are doing nothing.
I am told this heater-(prh11- 2008 model- purchased at walmart for about $27.00)
- Had wiring that wasn't up to standards
-1/10,000 units cause fires
-something wrong with the heating element-stops working
- wouldn't stand level
-fires like mine have happened to a few other people
This came directly from a person at Jarden corporation(aka patton-sunbeam)
on Dec 23, 2012
Are the thermostat knobs replacable?
Yes, they should have a set screw built in, or they will simply pull off without much effort. If the knob does not pull off without much resistance, then look around it for a hole with a allen screw inside. If this is the case, just loosen the screw and the knob will come off no problem.
on Mar 03, 2011
Which is the higher setting
Sorry to read about your problem, I hope this helps you out.
I tried to help you. Please help me and Rate/Vote on my response. We take the time to answer your question. take the time to rate us.Thanks and good luck
4 Thumbs - Very Helpful
3 Thumbs - Helpful
2 Thumbs - Somewhat Helpful
1 Thumb - Not Helpful
on Dec 27, 2010
Not finding what you are looking for?